Text for tenders: Smart Package W x H x D = 600 x 2100 x 1200 mm (42 U)


Smart Package W x H x D = 600 x 2100 x 1200 mm (42 U)



Frame: Symmetrical extrusion frame made from welded and

vertical 16-fold hollow sections with 25 mm DIN pitch

pattern punchings, system punching integrated in the

frame section, all section edges are rounded, vertical

frame sections each have two depth-offset vertical

mounting levels, the horizontal 9-fold sections have an

additional protection channel fitted above the seal.

Enclosure baying is possible at all levels.

Doors: Sheet steel front and rear doors, extensive

perforations, free surface area of 78% in the

perforated part of the plate.

The doors are reinforced by a rectangular frame with 25

mm DIN pitch pattern punchings, 4-point locking rod,

comfort handle with 3524 E security lock.

A semi-cylinder can also be fitted (40/45 mm) as per

DIN 18254.

The hinge is fitted on the right and has captive hinge

pins, the door stop can be changed without having to

remove the locking rods, 130° opening angle

(upgradeable to 180°).

Roof and base: Roof plate has 4 cable entry round holes

in the corners.  These are sealed by plastic caps.

Open base, solid plinth including fitted levelling

feet.

Side panels:

Side panels screwed on to the enclosure frame, included

in the package.

All of the screwed on panels have automatic potential

equalisation, includes enclosure panel earthing as well

as a central earthing connection point.

Interior installation: 482.6 mm (19") levels fitted at

the front and rear using mounting frames; front and

rear as per EIA 310-D, linearly depth-adjustable

Maximum 19" level static load: 1000 kg

2000 mm long PSM busbar system with 7 standard sockets

fitted using a fixed installation kit. 1 x earthing-pin

module (4 x sockets) and 2 x IEC modules (IEC320, in

total: 12 sockets) included in the package.

Included valuable accessories:

3 m long connection cables (1-phase / 3-phase with EU

type IEC309 CEE plug) for the PSM busbar.

Cable shunting ring 125 x 65 mm (10 x)

1 U blanking panel, toolless fixing (10 x)

1 U cable management panel  (2 x)

EN60320 C13 cable clamp  (IEC connection cable, 20 x)

19" plug-in captive nut (50 x)

Material: Sheet steel

Surface finish: Electrophoretic dipcoat-primed

Flat surfaces powder-coated in textured RAL 7035

Zinc-plated mounting frame, passivated

Dimensions (W x H x D): 600 x 2100 x 1200 mm, 42 U



Manufacturer: Rittal
Type: Smart Package W x H x D = 600 x 2100 x 1200 mm (42 U)    7996585
or equivalent


Quantity  Unit         Price Each                 Price Total
   
_____     ______       ____________               ____________
