Text for tenders: 4.5kVA UPS, 2 U


4.5kVA UPS, 2 U

Double conversion technology (online technology)

protects the connected electrical components against

hardware damage or data loss. The possibility of a

rack or tower arrangement offers a high degree of

flexibility. The LCD display with operating buttons

which can be rotated through 90° makes ergonomic

operation possible in all installation positions. All

of the final units are supplied with current of a

consistent quality by the generated sinusoidal AC

voltage. The software included in the package also

enables the operating status to be displayed and a

fully automatic shutdown of servers to be implemented.

Technical specifications:

- Dimensions 482.6 mm (19"), 2U, 660mm depth

- Can be used in the form of rack or tower UPS

- LCD display which can be rotated

- Weight 24kg

- Power output 4500VA/3150W

- Input 230 (160 . 288) V AC/50-60Hz +/- 5%

- Output 220/230/240 +/- 1%

- Synchronised frequency 50/60Hz +/- 1Hz

- Free-running frequency 50/60Hz +/- 0.2%

- Power factor > 0.99

- Compact connector

- Online technology

- internal electronic bypass

- serial interface RS232

- USB interface

- EPO (Emergency Power Off) contact

- up to 3 additional battery packs 2U

- optional relay-, SNMP or AS400 card

Compatible for Rittal CMC-TC monitoring

- VFI-SS-111 classification code

- IEC 62 040-3 and VDE 0558 part 530 standards

Note:

No batteries are fitted in the UPS control unit. At

least one battery pack (2 U) must also be ordered.



Manufacturer: Rittal
Type: 4.5kVA UPS, 2 U   DK 7857433
or equivalent


Quantity  Unit         Price Each                 Price Total
   
_____     ______       ____________               ____________
