Text for tenders: TopTherm roof-mounted cooling unit,


TopTherm roof-mounted cooling unit,

designed especially for office applications

Useful cooling output as per DIN 3168 L 35 L 35

1100/1200 W

Dimensions W x H [mm] 597 x 415 x 475

Rated operating voltage: 115V, 1 ~, 50/60 Hz

Power consumption Pel to DIN 3168 L35 L35, 790/810 W

Refrigerant R 134 a

Temperature range 20°C - 55°C

Temperature control and monitoring via

comfort controller with two floating fault signal

contacts and connection for door operated switch

Factory setting 35°C

Electronic condensate evaporation and RiNano coating

Connection via terminal strips

Protection category to EN 60 529/10.91

External circuit IP 34/ Internal circuit IP 54

Colour RAL 7035.

Weight 47 kg



Manufacturer: Rittal
Type: TopTherm roof-mounted cooling unit,   SK 3273515
or equivalent


Quantity  Unit         Price Each                 Price Total
   
_____     ______       ____________               ____________
