Text for tenders: TopTherm roof-mounted cooling unit,


TopTherm roof-mounted cooling unit,

designed especially for office applications

Useful cooling output to DIN 3168 L 35 L 35

1100/1200 W

Dimensions W x H [mm] 597 x 417 x 475

Rated operating voltage: 230 V, 1 ~, 50/60 Hz

Power consumption Pel to DIN 3168 L35 L35 760/780 W

Refrigerant: R 134 a

Temperature range °C

+20°C to +55°C

Temperature control and monitoring via

comfort controller with two floating fault

signal contacts and connection for

door operated switch

Factory setting 35°C

Electronic condensate evaporation and RiNano coating

Connection via terminal strips

Protection category

to EN 60 529/09.2000

External circuit IP 34/ Internal circuit IP 54

Colour

RAL 7035

Weight

42 kg



Weight 42 kg



Manufacturer: Rittal
Type: TopTherm roof-mounted cooling unit,   SK 3273500
or equivalent


Quantity  Unit         Price Each                 Price Total
   
_____     ______       ____________               ____________
