Text for tenders: 2kVA UPS, 2 U


2kVA UPS, 2 U

The 19. UPS with integrated batteries and double-

conversion technology (online technology) protects the

connected electrical components against hardware

damage or data loss. The possibility of a rack or

tower arrangement offers a high degree of flexibility.

The LCD display with operating buttons which can be

rotated through 90° makes ergonomic operation possible

in all installation positions. All of the final units

are supplied with current of a consistent quality by

the generated sinusoidal AC voltage. The software

included in the package also enables the operating

status to be displayed and a fully automatic shutdown

of servers to be implemented. Two programmable outlets

for the switching on and off of connected loads are

available.

Technical specifications:

- Dimensions 482.6 mm (19""), 2U, 650mm depth

- Can be used in the form of rack or tower UPS

- LCD display which can be rotated

- Weight 29.4 kg

- integrated battery (service life of five years

according to euroBAT)

- Autonomy time 7/16 minutes (at 100/50 percent load)

- Power rating 2000VA/1400W

- Input 230V AC (160-280 V)/50-60Hz +/- 1Hz

- Output 220/230/240 +/- 1%

- Synchronised frequency 50/60Hz +/- 1Hz

- Free-running frequency 50/60Hz +/- 0.1%

- Power factor > 0.99

- Input socket 1xIEC 320 C14

- Output sockets 4xIEC 320 C13

- Output sockets 2xIEC 320 C13, programmable

- Online technology

- internal electronic bypass

- serial interface RS232

- USB interface

- EPO (Emergency Power Off) contact

- optional relay-, SNMP or AS400 card

Compatible for Rittal CMC-TC monitoring

- up to 2 additional battery packs 2U

- VFI-SS-111 classification code

- IEC 62 040-3 and VDE 0558 part 530 standards



Manufacturer: Rittal
Type: 2kVA UPS, 2 U   DK 7857431
or equivalent


Quantity  Unit         Price Each                 Price Total
   
_____     ______       ____________               ____________
