Terminal box Form 4b for modular outgoing section
Model No. SV 9674.703
For modular outgoing section, for shielding the connections (terminals) of the functinal space, busbar space and cable chamber.
+ Also required
+ Product description
For shielding the connections (terminals) of the compartment, busbar space and cable chamber in accordance with Form 4b to IEC 61 439-2. The terminal boxes are externally mounted on the compartment side panel modules (for internal compartmentalisation) in the cable chamber to match the heights of the compartments. If necessary, a clamping strip may be mounted on the cable retainer included with the supply.
Sheet steel, 1.5 mm
For installation of the terminal boxes, the width of the cable chamber must be at least 400 mm
Width: = 400 mm
Width: = 600 mm
Note: Enclosure width of the cable chamber
|To fit compartments:||
with height: 300 mm
|Customs tariff number:||
SV Terminal box Form 4b, for compartment H: 300 mm
– Customers who were interested in this item were also interested in
Maxi-PLS busbar, E-Cu for Maxi-PLS 45 system
Model No.9640.311Air circuit-breaker support bar
Model No.9673.004Compartment side panel module for internal compartmentalisation
Model No.9673.041Gland plate for compartment side panel modules (internal compartmentalisation)
Product data (ZIP)
Rittal does not assume any liability for the topicality of the data downloaded locally on your device.